CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||9 February 2004|
|PDF File Size:||18.10 Mb|
|ePub File Size:||17.86 Mb|
|Price:||Free* [*Free Regsitration Required]|
As we noted on the Services page, very few of the service agencies which are engaged in providing annual testing actually perform this to the level required by the Standard. Sprinkler System Testing Luc System in service on inspection?
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Annual Special Inspection Contact Person: Fire Alarm System Inspection Services. Check heat trace controller interconnection to fire alarm system.
Description of the area or fire zone protected by each alarm detection circuit this may be s36 the form of a list or plan drawing. X Coded signal sequences are not interrupted by subsequent alarms.
Standards Council of Canada
The applicable reports indicated below are attached hereto and comprise pages. Seconds Are the results comparable to previous test? Check relief port on pressure reducer valves are not leaking?
Record of broken mains in the vicinity? Hydraulic name plate is properly affixed to the csn riser? Test circuit breakers and fuses for proper operation? Alarm device, test on dry pipe, pre-action or deluge system using bypass?
Sprinklers and spray nozzles protecting commercial cooking equipment and ventilating systems replaced except for bulbtype which show no sign of grease buildup? Except where water cannot be discharged, test all systems simultaneously.
Free from mildew, cuts and deterioration?
The communicator is trouble free. Displays dan visible in the installed location. Gauges on dry system no low pressure alarm? Instructions for silencing the trouble signal and action to be taken when the trouble signal sounds. Control panel bonded to ground. Communication control enclosure bonded to ground.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Audibility of alert, alarm and voice messages checked. Main Power supply failure trouble signal operates. In this instance the detectors are powered by a stand-by battery that will ensure continued protection even in the complete absence of electrical power or a “brown-out”.
Battery Type as installed: J Upon failure of one amplifier, cna automatically transfers to backup K amplifier s. F Confirm that the alarm transmission to the fire signal receiving centre is received.
Sprinklers shall be inspected from floor level?
Diesel Natural Gas Other: Extinguishing ylc controlled by fire alarm system? Pressure reading at hydraulically most remote nozzle: Individual alarm and supervisory input zone clearly indicated and separately designated.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Description of alarm signal operation. It might be a good idea to suggest that they practice their individual escape cah during the test as well.
Ancillary functions visual indicators operates. The fire ylc system documentation is on site and includes a description of the system.
This type of detector is best used in residential applications, as it provides extremely good early warning to smoldering type fires that tend give off dense smoke and noxious fumes.
Circuits for emergency telephones for operation, including two-way voice M communication, operates.