CEI EN (Tab. 9). Current capacity: CEI UNEL /1 – CEI UNEL Rated voltage Uo/U: 0,6/1 kV. Max. voltage: 1,2 kV. Testing voltage: 4 kV. DC resistance: according to, CEI EN (Tab. 9). Current capacity: CEI UNEL /1 – CEI UNEL Rated voltage Uo/U: 0,6/1 kV. Max. voltage: 1,2 kV. T R ATOS FTG10OM/1 kV 4 X 2 5 CEI III CEI F2 UNEL /1. UNEL CEI / EN CEI EN EN
|Published (Last):||3 October 2015|
|PDF File Size:||5.41 Mb|
|ePub File Size:||9.13 Mb|
|Price:||Free* [*Free Regsitration Required]|
UNEL Specifies the identification of cores in electric cables. Specifies the test procedure and requirements for the assessment of the vertical flame propagation on single cables. Cables with flexible conductors for fixed wiring. Specifies the test equipment and method for the determination of the toxicity index of gases released during combustion of materials from cables. The cables are for connecting domestic appliances to the fixed power supply. See the list of positions currently available and fill out the job application form.
Provides guidance on using electric cables with an operating voltage up to 0. Single- or multi-core cables with flexible conductors for fixed wiring, with or without shielding. Cross-linked compound with low smoke, toxic and corrosive gas emission. Specifies the ageing conditions and procedures to be used for deriving thermal endurance characteristics of materials. Reaction to fire class: The cables are intended for interconnection of the production machines. Specifies the general requirements for high modulus EPR insulated cables for distribution, with operating voltage of 0.
Concerns the construction and testing requirements for single-core electric cables without sheathing and with halogen-free crosslinked insulation, suitable for fixed installations with particular fire behaviour characteristics.
Cables with rigid conductors for fixed wiring.
CEI Specifies the construction requirements, testing methods and requirements for fire resistant cables, for operating voltages from 1kV up to 3 kV.
Specifies ccei-unel test procedure for the assessment of flame spread of bundled cables, with non-metallic material of 1. Specifies the continuous current dei-unel for open air installation of power cables with operating voltages up to 1, V AC and 1, V DC. EN Describes the construction requirements, methods and test requirements for insulated and sheathed cables in the LS0H crosslinked compound.
Logistics unit Brendola VI: Specifies the test procedure for the determination of partial discharge for medium voltage cables. Specifies the electric cable designation symbols for energy, signal and cei-ubel for national cables. EN Specifies the equipment and method of test for the resistance to fire of cables having a diameter greater than 20 mm. Applies to oil-resistant flexible cables with insulation and PVC sheathing.
Single and multi-core with ceiu-nel conductors for fixed wiring. Describes the construction and size requirements of the 0. Describes the construction and size requirements of electric cables insulated with fire retardant PVC with reduced halogen emissions. Polyolefin-based thermoplastic with low smoke, toxic and corrosive gases emissions. Plastic material with low toxic and corrosive gas emission Specifies the construction requirements, test methods of G10 insulated cables which cei-unsl not propagate fire and generate low levels of toxic and corrosive gases halogen-freefor operating voltages up to 1kV.
Cei Unel Pdf Download
Corporate info La Triveneta Cavi s. EN Specifies the ageing conditions and procedures to be used for deriving thermal endurance characteristics of materials. Indicated for photovoltaic systems with a nominal operating voltage no greater than V in ac and V in dc. Type 1 and Type 2. Specifies the markings and classification of cables in relation to fire. Via Orna, 35 Multi-core flexible for fixed wiring.
UNEL Specifies the markings and classification of cables in relation to fire. Specifies the test method for the determination of corrosive gases HCI released during combustion of materials from cables.
EN Specifies the test procedure for the determination of degree of acidity corrosivity of gases, released during combustion of materials from cables, by measuring Ph and conductivity.
La Triveneta Cavi s.