EQJW Heating controller with digital user interface. Heating controller with communication capability for weather-compensating supply-temperature con-. Find out all of the information about the Fr. Sauter AG product: heating controller EQJW Contact a supplier or the parent company directly to get a quote or. View and Download Sauter Equitherm EQJW user manual online. Equitherm EQJW Temperature Controller pdf manual download.
|Genre:||Health and Food|
|Published (Last):||9 December 2018|
|PDF File Size:||18.26 Mb|
|ePub File Size:||9.24 Mb|
|Price:||Free* [*Free Regsitration Required]|
For a change SEtthe rest of the procedure is as described in the Section on ‘Entering a switching command’. Viewing Service Parameters Turn the input eqnw the value for the parameter is changed Push the input knob; the new value is confirmed Push the ESC button to cancel the procedure.
To print the manual completely, please, download it. Changing Communication Parameters Weekly Switching Programme Push the input knob; the time for the switching command is confirmed.
Overview Of Technical Data The recommended values have been tried and tested but they are not necessarily the ideal solutions for every plant. Access To Manual Mode Front View Of The Eqjw Displays For Modem Operation Modem Operation The line between the controller and the modem must not be longer than 1. Got it, continue to print.
Access To Communication Mode Weekly Switching Programme Explanations About Individual Communication Parameters Back-up mode means that the heating is switched off. Index Of Key Words Don’t have an account?
Set Valve Position Service level and communication parameters; contains all the other parameters heating characteristic, control parameters, communication settings, etc. While the time is running down, the remaining time is shown in days, hours or minutes. Page of 44 Go. Modbus Bus Wiring Table Of Contents Use the ESC button or set the rotary switch to another position to cancel the temporary temperature change function.
Details about the protocol extension are available on request.
The controller is then basically ready to use. Up-to-date information on this subject must be requested from the network operator.
Sauter Equitherm EQJW 125 User Manual
The value is not accepted unless it has ejqw been confirmed. Page 43 Software version Table Of Contents Calendar switching programme Sending And Receiving Outdoor Temperatures Push the input knob; the time for the switching command is confirmed. Synchronising The Time Display In Automatic Mode List Of Service Parameters If the room sensor fails, the controller operates according to the settings for operation without a room sensor.
Ending Manual Mode Some of the parameters cannot be changed – they can only be viewed version number, status information. The equitherm EQJW is a compact weather-compensating heating controller with switched outputs to control the flow temperature.
The equitherm EQJW is a quality product from one of the leading manufacturers of controls products for eqmw, ventilation and air-conditioning. Entering A Switching Command Viewing The Communication Parameters After the temporary temperature change has finished, the heating circuit is again controlled in accordance with the automatic mode. Modbus Data Points coils If coil register 4 is set, then coil registers 89, 90, 96 and are also set automatically as a result.
SAUTER EQUITHERM EQJW USER MANUAL Pdf Download.
Press the ESC button once before confirming to cancel the input; the old value is retained. Don’t show me this message again.
By pressing ‘print’ button you will print only current page. Turn the input knob; the value for the parameter is changed Push the input knob; the 1255 value is confirmed Push the ESC button to cancel the procedure. No guarantee is given of the availability and correctness of these numbers. Faults Flow temperature sensor: Explanations Of Service Parameters SP11 Correction of outdoor temperature The measured value for the outdoor temperature is adjusted with eqnw help of this parameter.
Enter text from picture: The data points are transmitted in 16 bits. Display of setpoint temperature; flashing: The value will not be accepted unless it has already been confirmed.